sewage treatment solutions
What Is A Percolation Test?
If the soil is suitable, a percolation test will then decide how large your soakaway system will need to be.
However, the percolation test is only the last of the three mandatory tests which assess your site:
- First, you must ensure that your site is not in one of the Groundwater Source Protection Zones. It is essential to protect those groundwater sources from contamination as they supply up to 80% of public drinking water in some areas of England.
- Secondly, you have to run the Trial Site Assessment Hole (TSAH) to determine the position of the groundwater table. The tests are part of the British Standards BS 6297:2007. See also the General Binding Rules: small sewage discharge to the ground of the Environment Agency.
- Thirdly, the percolation test, as outlined, is required.
It’s important to note that it is not recommended to carry out the percolation test during abnormal weather conditions such as heavy rain or drought as this will skew any results with unusual groundwater levels.
How to perform a percolation test?
A percolation test requires at least two test pits. Locate the test pits where you are planning to install the soakaway system and dig to the planned depth below ground. Dig the test holes, 300mm square to a depth at least 300mm below the required invert level of the infiltration pipe.
Once dug, you should fill them with water. If, after six to twelve hours, the water has not drained away, the percolation test has failed.
If the percolation has succeeded, fill the pits again with water and measure the time taken for the water to drop from 3/4 full (225mm) to 1/4 full (150mm) then divide this time by 150. The answer gives the average time in seconds (Vp) required for the water to drop 1mm. You have to repeat this percolation test three times in each pit.
How to calculate the required surface area for the soakaway system
Vp = The speed at which the water in the test holes percolates through the soil.
- Any result between 15 and 100 seconds means that the ground should be suitable.
P = The maximum number of persons that the tank or plant is designed to serve
- Area (A) = Vp X P X 0.20 – for sewage treatment plants
- Area (A) = Vp X P X 0.25 – for septic tanks
The result (A) will be the area in m2 required for the soakaway system. Our installer will perform further calculations to find out the length of pipes required.
How does a soakaway system work?
The solids from the sewage sink to the bottom of your septic tank, or packaged treatment plant, and get removed when the tanks are emptied every 3-5 years. Licensed waste disposal companies do provide this maintenance service in the UK if you need it.
Why is the type of soil of my property so important?
For example, soil which is mostly clay based is usually not suitable for a soakaway, as it is not porous and won’t allow the sewage to pass through it. Blue clay is quite common in the UK.
Likewise, fine sandy soil is going to drain water away much faster, which might prevent adequate treatment.
Furthermore, soakaway systems do not get installed under driveways, parking areas, buildings or near trees, dwellings, boundaries, rivers and streams.
Call us at this number 0044 (0) 1934 422311 or drop us a message if you need any help with the paperwork involved with a percolation test.
Once you have recorded the results of your percolation test on this form, please send it to us along with the Environment Agency Consent to Discharge. We will then be able to install your new sewage treatment plant.
Get in touch
Tricel Environment UK
A trading brand of Dewey Waters Ltd.
Heritage Works, Winterstoke Road, Weston-super-Mare, BS24 9AN, United Kingdom.
Tel: +44 (0)1934 422 311